Remove 98+% of 0.01 micron particles and 100% of all visible particles
Remove liquid condensate at the same efficiency as for solid particles
Remove essentially all nonvolatile boiler feedwater additives
Comply with USFDA, USDA, Health Pro- tection Branch of Health and Welfare Canada, and 3-A accepted practices
Stop carryover of boiler feedwater chemi- cals
Absolute Filters- Steam Filters
Absolute's Series SR Filters are in full compliance with the requirements of the US Food, Drug and Cosmetic Act.
They also meet the regulations for Indirect Food Addi- tives used as Basic Components for Repeated Use Food Contact Surfaces as specified in 21 CFR Part 177, and Current Good Manufacturing Practices, 21 CFR Part 110. These filters have been accepted by the USDA for use in federally inspected meat and poultry
plants. Absolutes Steam Filters are in full compliance with the 3A Accepted Practices (Number 609-00) for produc- ing steam of culinary quality. They are also in full compliance with the requirements of the Health Protec- tion Branch of Health and Welfare Canada.
Absolutes Steam Filters eliminate particulate contamina- tion of food products caused by direct contact with dirty steam. Other benefits include: reduction in steam condensate mixing with food products when steam is used for agitating, mixing, or cooking; eliminate taste and odor problems by reducing boiler feedwater carryover; Reduced maintenance requirements.
The strainer shall be Series 723/793 Self- Cleaning, motorized type, as designed and part manufactured by FE and Absolute Filters The body and cover shall be fabricated (carbon steel) designed, manufactured and tested generally to ASME Section VIII standards, using qualified ASME Section IX welders. Housing to be suitable for a design pressure of 150 psig. Inlet and outlet connections shall be flanged and conform to ANSI B16.5 standards. The strainer shall have a single backwash connection and drain blowoff connection. Strainer to be complete with factory supplied steel support legs for bolting to concrete or steel base. Strainer shall be __________ size capable of handling __________ gpm of fluid at a _________ psig pressure loss with clean straining element. The straining element will be manufactured from corrosion resistant (304 stainless steel) reverse rolled slotted wedge wire screen designed with ___________ inch openings. The wide or flat cross section of the wedge wire shall face the direction of flow providing for a continuous smooth flat surface to trap debris. The straining media shall be free of pockets, tubes, collector bars, etc. that accumulate and trap debris permanently. All internal parts will be corrosion resistant (stainless steel). The strainer shall be provided with drive shaft and hollow port assembly fitted with all necessary bearings and seals. The drive arm and hollow port assembly including the adjustable accelerator plate will be free running at a maximum speed of two (2) rpm and will not contact the screen surface. Port assembly shall be factory and field adjustable for positive effective cleaning and shear capability.
- Filter bag hold-down devices
- Sanitary construction
- Different outlet connection
- Higher pressure ratings
- Extra-length legs
- Heat jacketing
- Duplex units