Duplex filters permit continuous operation, reducing overall operating costs. Flow can be switched back and forth between two filter vessels or housings, allowing one side to be serviced while the other is in use.
The Absolute duplex, using a single multi-ported valve operating system (patent applied for), is a better solution, and offers many benefits:
- Four separate valves are used all oper- ated simultaneously by a single lever.
- Valves use the standard butterfly design, known for their effective seal, low pressure drop, and low cost.
- Any of the valves can be serviced individually, without need to disturb the other valves or piping. Replacements are readily available.
- Valves are soft-seated to provide bubble-tight closure.
- A variety of valve seal materials is available for use with a number of hard-to-handle fluids.
- Pressure drop is minimized because the flow path has the equivalent of only four elbows instead of the usual six.
- Mechanical stops assure that the valves are completely open or closed.
- A single-valve pressure balancing vent system is furnished to ease movement of the lever and to fill the just serviced vessel before use.
- Vents in filter covers and drain ports in filter housing speed evacuation and filling.
- Remotely operated power actuators and automatic power actuation (triggered by pressure differential sensing) are offered. Air or electric actuation is best if such power is available.
- Available in carbon steel, 304 stainless steel, or 316 stainless steel.
- Internal valve parts other than seals are 316 stainless steel.
- Four different materials can be ordered for all seals involved.
- All baskets and mesh linings are made of stainless steel. 304 stainless will be supplied with carbon and 304 housings, 316 stainless with 316 housings.
Choosing a Basket Strainer or Bag Filter
Choose between straining a fluid (removing particles down to 74 micron size) and filtering it (removing particles down to 1 micron).
Pressure Drop Data
Basket strainers and bag filters are usually selected so that the pressure drop does not exceed 2 psi, when they are clean. Higher pressure drops may be tolerated, when contaminant loading is low.
The pressure drop data are accurate for all housings with strainer or filter bag baskets. When filter bags are added, total pressure drop becomes the sum of the pressure drop as determined by the steps below plus the pressure drop through the bag as defined on pages 61 and 62.
Follow these easy steps:
- Using the desired pipe size and approximate flow rate, determine the basic pressure drop from the appropriate graph.
- Multiply the pressure drop obtained in step 1 by the viscosity correction factor found in the accompanying table. This is the adjusted (clean) pressure drop for all baskets without filter bags.
Note: Filter bags are specified separately. See page120-130.
Build an ordering code as shown in the example.